Electrex Femto D4
Product and variants: Femto D4
Description: Femto D4 is a three-phase DIN-rail energy analyzer.
Measures: Electrical parameters
Compatible using: DEXGate
Electrex Femto D4 - Quick Install Guide
To follow this guide you will need:
- 1 x DEXGate
- 1 x Femto D4
- 1 x USB-RS485 addapter
- 1 x Computer
- 1 x Ethernet Cable
- Install the current transformers following the following diagram:
- Connect the orange usb cable to the A connector, the yellow cable to the B connector and the black cable to the GROUND connector:
- Power up the meter
- Access to set up menu and configure ModBus address.
- Configure current transformers factor
- Reset meter values
- Power up the DEXGate
- Connect the USB-RS485 cable to the DEXGate
- Connect the Ethernet cable to your computer and the ETH1 port of the DEXGate
- Access the web administration interface of the DEXGate (http://172.16.0.1)
- Login (the default username and password are admin/admin)
- Go to the "Bridge Configuration" section
- Edit the line:
to look like this:
- It means that there is a Femto in ModBus adress 10.
- Restart the modbus bridge or the DEXGate
- You're done!